APRIL POINT DEVELOPMENTS SOUTH END WATER
1222 April Point Road
Current Hazard Rating
This facility is currently under a .
- Underlying Problems: ["Unapproved source"
- Underlying Problems: " Other - Unapproved source"
- Underlying Problems: "Not permitted under Drinking Water Protection Act"
- Underlying Problems: "Ownership management unclear"
- Underlying Problems: "Not maintaining monitoring"
- Underlying Problems: "bacteriological counts"
- Underlying Problems: "issues with boron and arsenic"]
- Steps Taken to Remedy: 2 homes on system not using water for potable purposes. Need t omake application for source approval. Need to make application for construction approval to upgrade treatment for pathogens, boron and arsenic. Need to maintain routine monitoring requirments.
- Corrective Actions Remaining: N/A
Facility History: Click on an inspection link below to see additional details.
1-Jan-2022 to 31-Dec-2022
1-Jan-2021 to 31-Dec-2021
1-Jan-2020 to 31-Dec-2020
1-Jan-2019 to 31-Dec-2019
1-Jan-2018 to 31-Dec-2018
1-Jan-2017 to 31-Dec-2017