This facility was given a High hazard rating. More info
January 23, 2019
Number of critical violations
Number of non-critical violations
A summary of the violations found during the inspection are listed below.
Critical Interruption of Treatment
Non-Critical Inadequate Microbiological Analysis data
Non-Critical Inadequate Chemical Analysis Data
The Water System consists of a surface source, 50/5 micron + 1 micron absolute cartridge filters and UV disinfection.
An Emergency Response Plan is posted in the treatment building along with procedures to be followed in the event of a boil water advisory. The plan must be reviewed regularly to ensure it is up-to-date if any changes are made, updates must be forwarded to the Environmental Health Officer.
The Water Operator has completed the Water Safe training course proof of completion (certificate) must be forwarded to the Environmental Health Officer (EHO).
An Annual Report was not completed for 2017 the annual report for 2018 must be completed and provided to the users of the water system and the EHO by June 30, 2019.
Records of all maintenance carried out on the system must be maintained
including the date of all filter and bulb changes.